7.5 Amps of current leaving this Clubhouse Service Entrance is going back to PG&E via a different route, it could be a Neutral to Neutral or Neutral to Ground connection with the separate Service Entrance on the dormitory.
NOTE: net current is reduced to .53 amps when the 100 amp Clary Suite sub panel, which is daisy chained, is turned OFF at the Laundry Room sub panel.
At the Clary site sub panel, circuits are creating Severe to Extreme concern magnetic fields in the living room, kitchen entry and has to the suite itself.
This hazardous condition creats a fire, shock and magnetic field health risk. It must be fixed and brought back to code.
It is hard to believe that this work was done by competent electricians or was properly inspected.
ric Windheim BA, EMRS, BBEC, RFSO
Certified: Electromagnetic Radiation Specialist
& Building Biology Environmental Consultant
Windheim EMF Solutions
Please use the “Contact Form” on the site in order to serve you best.